Detail SEPAM 1000+ Relay Overcurrent And Undercurrent Protection Relay
Sepam series 20
Suitable for common applications, Sepam series 20 offers simple solutions
based on current or voltage metering.
b protection of substation incomers and feeders against phase-to-phase and
v 16 IDMT tripping curves
v adjustable timer hold to detect recurrent faults
v switching of groups of settings to adapt to changes in the network configuration
b protection of overhead lines with built-in recloser function
b protection of transformers against overloads, with ambient temperaturecompensated
RMS thermal overload protection with 2 groups of settings for different
ventilation operating rates
b protection of motors
v against overloads, with ambient temperature-compensated RMS thermal overload
protection with a cold tripping curve that can be adjusted to fit motor characteristics
v against internal faults and load-related faults
v with motor starting condition monitoring and machine operation assistance.
The Sepam series 20 B21 and B22 voltage units are suitable for the following
b monitoring of network voltage and frequency
b loss of mains detection by rate of change of frequency protection for installations
with local power generation.
Sepam series 40
Sepam series 40, with its current and voltage metering capabilities, offers highperforming
solutions for more demanding applications.
Sepam series 40 units perform the following funcitons in addition to those performed
by Sepam series 20:
b protection of closed ring networks or networks with parallel incomers, by
b directional earth fault protection suitable for all earthing systems: impedant,
isolated or compensated neutral
b protection of networks with variable configurations requiring the switching of
groups of settings and logic discrimination
b all the necessary electrical measurements: phase and residual currents, phase-toneutral,
phase-to-phase and residual voltage, frequency, power and energy, ...
b comprehensive network diagnosis assistance: 20 seconds of disturbance
recording, detailed history of the last 200 alarms, storage of the last 5 tripping
b adaptation of control functions by a logical equation editor
b customization of alarm messages to fit each application, and/ or in the user’ s